External grounding of shop.
Remove ground rod assembly from storage
Power on to shop.
1. A qualified electrician will make connection
of main power cable (1) from shop (2) at power
distribution panel (3).
2. Shop personnel will move the main circuit
breaker (4) in the circuit breaker panel (5) from OFF to
3. See that all other circuit breakers are in the
2-6. Other shop utilities.
In addition to electrical power the shop is provided
with connections for compressed air and water.
Compressed air connection.
1. Remove protective dust cap (1) from air inlet
nipple (2) at the service utility panel (3). Store in shop
Change 2 2-18.1/(2-18.2 blank)
|Integrated Publishing, Inc.|